Parallel Machine Control System: When customers need to purchase multiple gas generating units to operate simultaneously, it can provide customers with automatic and manual combined cabinets. It can also set up automatic load distributor according to customers'request to ensure that all units are loaded and run smoothly.
Through the use of different control systems, the customer's different requirements for the control system are satisfied.
Grid-connected control system: When customers need to purchase one or more gas generating units for grid-connected operation, it can provide customers with automatic and manual grid-connected cabinets.
DCS control system: when customers need to purchase multiple gas generating units for centralized or decentralized operation and demand centralized monitoring by upper computer, it can provide customers with centralized control cabinet with DCS function to complete monitoring, remote control, data storage, report printing and other functions.
Basic control system: using t2l0 or function-matched control module and response sensor to complete the display of speed, power, voltage, current, power elements, frequency, oil pressure, water temperature, oil temperature and other parameters. Low oil pressure, overspeed alarm stop, high water temperature alarm stop automatic control. It can communicate with the host computer through RS232 or RS485 communication interface. The exhaust manifold temperature and turbine front and rear temperature of the gas engine are inspected by the exhaust temperature patrol instrument.
With the advanced three-dimensional design software, we can fully integrate the profound design with the meticulous and dedicated body, so that our products can be compared with the products of world famous large companies in terms of performance, morality and appearance.
Three-dimensional design software is used to design:
By using the waste heat recovery technology of gas generator, the comprehensive thermal efficiency of gas generator unit is not less than 80%. According to the user's request, the exhaust heat of the gas generator can be used, the medium temperature and medium pressure waste heat boiler and steam turbine generator set can be set up reasonably, and the gas-steam separation cycle can be used to generate electricity. According to the user's request, the waste heat from exhaust gas of gas generator can be used to set up lithium bromide units reasonably to supply customers with cooling and heating sources of central air conditioning. According to the user's request, the exhaust heat of the gas initiator can be used, and the heat exchanger can be reasonably set up to supply the domestic heating and hot water for customers. The exhaust gas of the initiator after the application of the residual heat can be used as the heat source for drying, so as to improve the comprehensive utilization efficiency of the gas.
For the users who have strict noise control in the near and left situation of the unit, we can supply the ordinary silent skid-mounted gas-fired generating units to the users to ensure that the noise at the 1-meter sound field is less than 82 db. If the users demand more stringent noise control for the unit, we will adopt more stringent noise reduction methods according to the users'request.
For the users who need to put gas generating units in the open air in the inorganic room and do not have strict noise control in the near future, we can supply rain canopy type or standard container type skid-mounted structure units. The users can install power generation only by supplying the response area to reach the horizon.
ATS control system: when customers need to use gas-fired generators as hot standby power supply for municipal power supply, it can provide control cabinets equipped with ATS to complete self-starting, automatic operation and closing power supply of gas-fired generators when municipal power outage occurs. When the municipal electricity is transmitted, the gas generating units are automatically switched off and the municipal electricity is automatically switched on and delivered.
The waste heat recovery technology of the starter is adopted.
Through the use of skid-mounted structures in various situations, we can satisfy customers'demands for different uses and different places. For users with fixed computer room and less strict noise control in near-left situation, we can provide users with ordinary common base type skid-mounted structure units with lower skid-mounted cost.